Kuparuk 2M-Pad Pipeline Release
- Time/Date of Incident
- Spill Number
- The investigation team has determined that internal corrosion of the pipe wall was the cause of the spill. CPAI is continuing to perform a comprehensive ‘physical causes failure’ analysis and additional evaluation of the affected pipe. ADEC staff from the Prevention Preparedness and Response Program are monitoring this analysis to ensure prevention measures are implemented as necessary.