Site Report: Duffys Roadhouse
|Site Name:||Duffys Roadhouse|
|Address:||Mile 62.7 Tok Cutoff; SR Box 370, Gakona, AK 99586|
We make every effort to ensure the data presented here is accurate based on the best available information currently on file with DEC. It is therefore subject to change as new information becomes available. We recommend contacting the assigned project staff prior to making decisions based on this information.
Contamination still remains in 12 ft. long pit because backhoe could not reach further. Hung was lead.
|Action Date||Action||Description||DEC Staff|
|3/5/1993||Leaking Underground Storage Tank Release Confirmed - Petroleum||LUST Site created in CSP for source area ID 76184 ADD;||* Not Assigned|
|3/5/1993||Site Added to Database||* Not Assigned|
|2/13/1996||Underground Storage Tank Site Characterization or Assessment||SA1; DEC rec'd 11/17/95 closure site assessment on 11/20/95.||* Not Assigned|
|6/25/1996||Leaking Underground Storage Tank Cleanup Initiated - Petroleum||LCAU; (2) 2,000-gallon unleaded gasoline USTs removed 10/13/95 along with 30 cubic yards of contaminated soil. USTs initially stored leaded gasoline. Soils will be bioremediated/aerated on-site.||* Not Assigned|
|1/13/1997||Release Investigation||SA2A; RPCON instructed by DEC via phone to conduct further investigation on depth of soil contamination above ADEC cleanup levels left in pit 10/95. Submit work plan for DEC approval.||* Not Assigned|
|1/16/1997||Release Investigation||LCAR; Work plan for RI submitted and approved for field work 1/20/97. Soil sample results of 2 SBs 25 & 30 ft. indicated levels below ADEC cleanup levels. Two soil samples from 35 cu. yds. stockpiled soils from UST excavation(sampled 10/95) were below ADEC cleanup levels.||* Not Assigned|
|2/10/1997||Site Closure Approved||CLOS; Closure letter issued. Comments: Rush 3/3/97 preliminary closure ltr. by DEC at request of RP not accepted by buyer. Buyer wanted final ltr. issued 2/10/97 describing in detail cleanup actions conducted.||* Not Assigned|
|For more information about this site, contact DEC at (907) 465-5390.|
|No ICs Required|
|Advance approval required to transport soil or groundwater off-site.|
There are no documents for this site report.